Devices of a priority of power with the EK-24 MT relay
Devices of a priority of power with the EK-24 MT relay are intended for priority power distribution on three group lines (it is possible smaller), with automatic shutdown of lines of the lowest priority at emergence of the general overload in a network and automatic connection of the disconnected lines, after disappearance of a condition of an overload. Are used if the total power of the connected loadings surpasses the allocated power, `knocking-out ` of the introduction machine gun because of an overload is thus prevented and guaranteed that any of lines doesn`t remain constantly de-energized! Devices with the EK-24 MT series relay also protects loadings from: overcurrents; raised andlowered tension; if necessary from differential current of leak. Devices of a priority of power with the EK-243 MT EK-241m MT relay - are used in that case when the total power of the connected loadings surpasses the allocated power, `knocking-out ` of the introduction machine gun because of an overload is thus prevented; - loadings are distributed on three group lines from the lowest priority to the highest, automatic shutdown of group lines of a low priority at overload emergence in networks and automatic connection of group lines of a low priority at disappearance of a condition of an overload is thus provided; - the system functions in a modededuction of the allocated power, is means that in the presence of constantly operating overload group lines of a low priority continue work in a periodic mode, receiving the electric power in the portions so that average consumption on input remains at the level of the allocated power, that is the system `extorts ` all allocated power and guarantees that any of group lines doesn`t remain constantly de-energized! - in a mode of deduction of the allocated power loadings are connected to group lines of a low priority allowing periodic inclusions switching off: systems of a termostatirovaniye, heating, street and garage lighting, to group lineshigh priority the powerful loadings of short-term action which aren`t allowing for action of shutdowns are connected: sunbeds, water heaters of boylerny type, electric stove, household appliances. Low-power loadings not allowing shutdowns in general (emergency lighting, the security and fire alarm system, video surveillance, electric locks) are connected bypassing system of priority distribution of power. The media household appliances including computers to be connected to the line of the highest priority; - full analog on Russian to a wound - No. Devices with similar that. characteristics and/or functionality 30% more expensive, than devices of a priority of power with the relayMT EK-241m of MT of EK-243. Price: contractual Priority distribution, management of power distribution, clever house, management of consumption, control relay priority, block of priority distribution of power, block of priority distribution, scheme block of priority distribution
City: Krasnodar Name: Napylova Natal`ya Petrovna Telephone numbers and addresses: 350072, Россия, г. Краснодар, ул. Солнечная, д.10 тел.: 8(861)243-02-13, факс: 8(861)243-03-70 Go to the web site: http://www.zprom.ru To the site of: 45 It is published: 2014-07-13 Viewings: 32 Visitors: 16
Number of your announcement - 135706!